Originally Posted by Rammer
I have a 3000SEI yamaha. The AC also will not run when connected to a building. It blew a 15AMP breaker in seconds
Won't run/start on a 15 amp circuit, it takes a 20 amp because of the start surge.
If you were told that it would run on a 15 amp circuit they told you wrong.
This is from the Coleman Spec sheet:
Use time delay fuse or circuit breaker (U.L. H.A.C.R. Type C.S.A.) Rated at 20 amps.
Supply wires 12 AWG Min. (Copper)