Originally Posted by Vicr
Hot and ground reversed or hot and neutral?
hopefully hot and neutral because if it is hot and ground it is a short... well last I checked...and if nothing works I would suspect there is a short somewhere..nothing works right?
you're going to need a voltmeter... and I would highly recommend a EMS if you are not familiar with electricity..
what is the amperage you are working with 50 or 30?